Surface areas should be dry, clean and sound, free of voids, sharp protrusions or contaminants. The surface shall have a light steel trowelled or fine wood float finish.
Substrate and Falls
Screeds are to be sand cement laid to minimum falls of 1 in 60, strength and thickness as per engineer’s specification. The moisture content is not to exceed 7% prior to torchon application.
Should light weight screeds be employed an additional sand cement screed is to be placed on top of the light weight screed, the strength and thickness as per the engineers specification. Under no circumstances must the torch-on material be applied directly onto the light weight screeds.
Special care must be given to all expansion/construction joints, refer to your a.b.e.® Technical Representative concerned for specific details.
Prime all surfaces with bitu.prime, including all verges, and around outlets and protrusions and allow the solvent to flash off. Extremely porous surfaces should be re-primed.
Strip existing waterproofing before priming all surfaces with bitu.prime, including all verges, around outlets and protrusions and allow the solvent to flash off. Some existing waterproofing materials may be overlaid only in consultation with the a.b.e.® Technical Representative concerned.
- a.b.e.®dex unigum 4 mm
- a.b.e.®dex unigum 3 mm
- ecofelt membrane
Full bore outlets, pipe upstands to have a square metre a.b.e.®dex unigum 4 mm bonded to the surface including their gussets. All internal and external corners to have a gusset fitted, 100 mm x 100 mm, using a.b.e.®dex unigum 4 mm prior to the commencement of the waterproofing application.
Apply the first layer, a.b.e.®dex unigum 3 mm and 4mm to the floor substrateensuring the layers are fully bonded to the bitu.prime primed surface by means of ‘torch fusion’ using propane gas, having side and end laps of 100 mm and 150 mm respectively.
Apply a coat of duraflex® incorporating ecofelt membrane extending at least 100 mm horizontally and vertically in the corner joints.
abedex waterproofing membranes shall only be warranted when installed by a.b.e.® Construction Chemicals accredited contractors.
Care must always be taken when working with open flames, potential fire hazard, and molten bitumen from the process, employ safety equipment and clothing where necessary.
All products are to be applied in accordance with the manufacturers instructions.
All relevant data sheets are to be carefully read for additional information.
This data sheet is issued as a guide to the use of the product(s) concerned.
Whilst a.b.e.® endeavours to ensure that any advice, recommendation, specification or information is accurate and correct, the company cannot – because a.b.e.® has no direct or continuous control over where and how a.b.e.®’s products are applied – accept any liability either directly or indirectly arising from the use of a.b.e.®’s products, whether or not in accordance with any advice, specification, recommendation or information given by the company.